- Account Services
- Customer Engineering Services
- Food Technology Centre
- Healthcare Services
- Industrial Equipment Hire
- Manufacturing Technology Centre
- Mobile Cryotherapy Chamber
- On-Site Gas Generation
- Refrigerant Services
- Risk Management Services
- Safety Training
The British Compressed Gases Association (BCGA) recommends that pressure regulators are refurbished or replaced with new at least every five years.
Depending on gas properties, the type of application and the frequency of use, this could be necessary more often; for example every 12 to 18 months for some particularly corrosive HCl systems.
BOC Inspection and Repair service
In response to the BCGA recommendations and the requests of many of our customers, BOC offers a comprehensive inspection and repair service for products supplied from the BOC Speciality Gases equipment range.
Our service covers both planned and unplanned maintenance and includes:
- certified external inspection, pressure/performance testing
- refurbish/repair-certified internal inspection, new active components, pressure/performance testing and 'same as new' warranty
Repairs are charged on a fixed-price basis which includes labour and specific, routinely changed components.
An additional charge will apply for the replacement of non-routine components.
While in service, we would recommend that regulators are routinely checked as follows:
Apply leak detection fluid around pressurised joints. If any bubbles form, this indicates a leak. No attempt should be made to rectify leaks while the equipment is under pressure.
Seat leakage or creep
Under normal conditions the outlet pressure indicated by the outlet gauge should remain steady. If this pressure rises over a one to two minute period there may be seat leakage. This may be due to particulate contamination within the regulator nozzle.
Needle movement around the dial should be smooth.
We would recommend that regulators are removed from service and tested annually, as follows:
Test, as above, at the maximum deliverable outlet pressure of the regulator. The outlet shut-off valve should also be tested for seat leakage.
Seat leakage or creep
Test, as above, for a minimum of one hour.
Further inspection and repair information
Never carry out repairs or modifications to BOC Speciality Gases equipment or change the gas service without express written permission.
If repairs or modifications are made without permission, BOC will not supply spare parts since repairs performed without the necessary tools, knowledge and facilities can result in unsafe equipment and the risk of failure.
ALWAYS specify the gas service for which the equipment is intended and NEVER change the gas service without first consulting BOC Speciality Gases.
If you wish to send your regulator to us for inspection or repair, please complete the equipment inspection/repair form.